Wi-Fi RIB relay AX Control
Using the http Get request program to turn on/off a Wi-Fi RIB relay using a Tstat Block
Follow the manufacturer's instruction on configuring your RIBTW2401B then download this .bog file and place it anywhere on the Config container in an Ax Jace. Navigate to the Property Sheet of the component and configure the IP address that you will use for each relay. (Static IP addresses are needed for each relay.) The address format for the string point on the property sheet should be "http://192.168.1.x"
This version is an example of using a 10k T2 sensor on UI1 and a kitControl Tstat block to start/stop a cooling fan.
The Functional Device RIBTW2401B is an 802.1 Wireless relay with one digital, and two universal inputs. The relay can be controlled with HTTP commands and has numerous use-cases. Turning on parking lot lights, exhaust fans, etc.
Copyright 2021 Albert Welch