Accumulates the total number of pulses on a digital input. When used in conjunction with a persistant point, the value holds through power cycles.
Drop on EC-GFX program
Drop on programming sheet of distech controller, and tie the Analog Value "number" value to the number input. This is the actual AV object value that is going to be totalizing all of the pulses. Tie the digital input that the meter is tied to into the variable value. Finally tie the the amount of gallons per pulse that the meter is scaled to.
Copyright 2020 Rob F.