Boiler Hot Water Temp Reset
A hot water reset control loop measures the outside air temperature
A hot water reset control loop measures the outside air temperature; this information is used to estimate demand for heating load as the outdoor temperature varies.
The hot water supply temperature set point is adjusted up and down in an inverse linear relation to outside air temperature.
The typical range for conventional boilers is to vary the supply water temperature set point from 140 to 180 °F (60 to 82 °C) as the outside temperature varies from 60 to 0 °F (16 to −18 °C)
The ZIP file contains a single BOG file. Extract and add the BOG to your station by dragging it from your files to the station via the Niagara Workbench Nav Tree.
Copyright 2021 Mark Mays
Mar 17, 2021