Supply Air Temp and Supply Static Reset
Use the MinMaxAvg Bql to query the VAVs for cooling signal to control the supply air temp setpoint of a unit. As the cooling signal from the VAVs increase, it resets to the lower setpoint. As the cooling signal decreases, it resets to the higher. The same is true for the supply static reset. The Bql is looking at the "need more air" signal from the VAVs.
Unzip the file. Paste the .bog in a folder on your C drive. Navigate to folder from Workbench/My File System/C and paste the .bog file in a wire sheet.
Using data from the VAVs, you can reset the supply temperature and supply static setpoints.
Copyright 2021 Jamie Pate